A type of air conditioning system using a water/glycol solution as a condensing medium. Typically, the glycol-cooled condenser is located inside the air conditioner with the rest of the refrigeration components. Water/glycol is piped to the unit from a drycooler or other suitable source. The glycol keeps the solution from freezing during winter operation.
A true central air-conditioning system uses ducts to distribute cooled air throughout the house. In a “split system,” the most common design, refrigerant circulates between an indoor coil and a matching—meaning from the same brand—outdoor condenser with compressor (see illustration, below). The refrigerant cools the air, dehumidifying it in the process; a blower circulates air through ducts throughout the house. A thermostat maintains the temperature at the setting you select. A variation is the “heat pump,” a type of system that functions as heater and air conditioner.
The main problem when installing a multi-split system is the laying of long refrigerant lines for connecting the external unit to the internal ones. While installing a separate split system, workers try to locate both units opposite to each other, where the length of the line is minimal. Installing a multi-split system creates more difficulties, since some of indoor units can be located far from the outside. The first models of multi-split systems had one common control system that did not allow you to set the air conditioning individually for each room. However, now the market has a wide selection of multi-split systems, in which the functional characteristics of indoor units operate separately from each other.
An air conditioner's compressor contains a refrigerant. As it works, it sends this refrigerant through the system. As warm air blows across the coil that carries this refrigerant, the heat transfers to the refrigerant (cool always absorbs warm). A fan moves the cooled air through the ducting and out of vents that lead into the rooms of your house. The refrigerant returns to the compressor where the absorbed heat is moved outside. The refrigerant is then sent through the coil once again to continue the cycle.