A more efficient method of controlling humidity is to use the waste heat from the refrigeration cycle itself. Instead of rejecting the waste heat outdoors, the heat is directed inside when humidity control is required. One form of heat reclaim is called hot-gas reheat or “refrigerant desuperheating” where refrigerant is passed through a heat exchanger located downstream of the cooling coil. The hot high pressure vapor leaving the compressor passes through this heat exchanger prior to entering the condenser coil. This in turn heats the indoor air and again causes the AC system to run longer to meet the thermostat set point. Although more energy is used, this is much more efficient than turning on an electric heater. Another form of heat reclaim is called sub-cool reheat. This strategy takes the warm liquid refrigerant from the condenser and passes it through a heat exchanger located downstream of the cooling coil. Less heat is available using this method because the majority of the heat has already been rejected at the condenser. Since more energy is used to pump liquid (as opposed to a gas) through the heat exchanger it would appear that this method is less efficient than the hot-gas method, however, the liquid in the heat exchanger is sub-cooled in the cold supply air stream which increases the capacity of the air conditioner. Since more capacity is available, the AC units is able to meet the thermostat more quickly.
An air conditioning system, or a standalone air conditioner, provides cooling and humidity control for all or part of a building. Air conditioned buildings often have sealed windows, because open windows would work against the system intended to maintain constant indoor air conditions. Outside, fresh air is generally drawn into the system by a vent into the indoor heat exchanger section, creating positive air pressure. The percentage of return air made up of fresh air can usually be manipulated by adjusting the opening of this vent. Typical fresh air intake is about 10%.
At Comfort Plus Services, we set ourselves apart from the rest through quality customer service across Salisbury, MD and surrounding areas. See our Areas of Service. Our strength is in our high standards of job performance and fully trained professionals. Our team upholds a proven reputation and is continually motivated to achieve excellence in every service we provide.
High-efficiency condensing furnaces (90% AFUE and above) are a bit more complex than conventional furnaces. The main differences between a conventional and condensing furnace are the heat exchanger technology used to extract heat from the combustion process and the method used to exhaust the combustion gases. In these ways, the furnaces are very different. The condensing furnace does not have a significantly more efficient combustion process than does a conventional furnace; both use gas burners with electronic ignition. The difference lies in that the condensing furnace has a more efficient heat extraction process after combustion.
Seasonal checks. Once a year have a licensed professional change all filters, clean and flush the coils, drain the pan and drainage system, and vacuum the blower compartments. The contractor should also check to make sure that the system is properly charged with refrigerant, that there are no leaks, and that all mechanical components are working properly.
This is a great option for cooling your home or business without having to deal with the ductwork. Other systems require ductwork so that the cool air can travel throughout the space. A ductless mini split air condition doesn’t require ductwork because it has an air conditioner or a heat pump outside that connects to units in the home that handle the cooling being pushed into them from outside. You can control the temperature of a whole home or just one room by controlling the air handlers in each specific area. This allows for more control and a more efficient way to control the temperature and cost of operating the ductless mini split air conditioner.
Indoor Fan Motor -- Indoor fans circulate the air from your house and through the system. Age and dust buildup are the two biggest contributing factors to their failure. When they are starting to fail they will often make noise. Failure of the fan will result in no heating or cooling, and if it is not repaired soon, it can cause other components to fail.
Tired of dealing with an inoperable furnace? Or, maybe your heating system is only heating half the rooms in your home? Whether you need a new heating system installed or an existing unit repaired, there’s only one name to know—ABC Plumbing, Heating, Cooling & Electric. With more than six decades of experience handling Chicago’s heating problems, our team at ABC has the experience and know-how to get any heating issue diagnosed and resolved quickly and efficiently.
As this liquid passes through the indoor cooling coil on the inside of the heat exchanger, two things happen to the air that passes over the coil’s surface on the outside of the heat exchanger. The air’s temperature is lowered (sensible cooling) and moisture in the air is removed (latent cooling) if the indoor air dew point is higher than the temperature of the coil’s surface. The total cooling (capacity) of an AC system is the sum of the sensible and latent cooling. Many factors influence the cooling capacity of a DX air conditioner. Total cooling is inversely proportional to outdoor temperature. As the outdoor temperature increases the total capacity is reduced. Air flow over the indoor cooling coil also affects the coil’s capacity and is directly proportional to the total capacity of an AC system. As air flow increases, the total capacity also increases. At higher air flow rates the latent capacity of the cooling coil is reduced. Indoor temperature and humidity also affect the total capacity of the AC system. As indoor temperatures increase, the sensible capacity also increases. Similarly, as indoor relative humidity increases the latent capacity of the AC system increases. Manufacturers of AC equipment typically provide a “performance map” of specific equipment to show how total, sensible, and latent capacity change with changing indoor and outdoor temperatures and humidity. Power consumption and energy efficiency are also provided in these charts.
Packaged terminal air conditioner (PTAC) systems are also known as wall-split air conditioning systems. They are ductless systems. PTACs, which are frequently used in hotels, have two separate units (terminal packages), the evaporative unit on the interior and the condensing unit on the exterior, with an opening passing through the wall and connecting them. This minimizes the interior system footprint and allows each room to be adjusted independently. PTAC systems may be adapted to provide heating in cold weather, either directly by using an electric strip, gas, or other heater, or by reversing the refrigerant flow to heat the interior and draw heat from the exterior air, converting the air conditioner into a heat pump. While room air conditioning provides maximum flexibility, when used to cool many rooms at a time it is generally more expensive than central air conditioning.
Vredevoogd Heating & Cooling invites you to research our good name. Read customer testimonials and call to discuss your service needs with our staff at any time. We provide service with minimal interruption to your home. We perform careful diagnostics and apply expert fixes for all your service needs. Because your HVAC system is essential to your home and a major investment, we encourage you to contact us for professional installation. We have 54 years of experience fueling our HVAC know how. Don’t trust your heating and cooling needs to just anyone. Let Vredevoogd Heating & Cooling Grand Rapids MI handle all your HVAC maintenance and installation needs.
It's a little awkward, so we'll get straight to the point: This Monday we humbly ask you to defend Wikipedia's independence. We depend on donations averaging about $16.36, but 99% of our readers don't give. If everyone reading this gave $2.75, we could keep Wikipedia thriving for years to come. The price of your Monday coffee is all we need. When we made Wikipedia a non-profit, people warned us we'd regret it. But if Wikipedia became commercial, it would be a great loss to the world. Wikipedia is a place to learn, not a place for advertising. It unites all of us who love knowledge: contributors, readers and the donors who keep us thriving. The heart and soul of Wikipedia is a community of people working to bring you unlimited access to reliable, neutral information. Please take a minute to help us keep Wikipedia growing. Thank you.
At the state level the rebates are still substantial. For example, switching to a zoned system can get you a $100 rebate from various A/C companies, and state rebates are also included. In Pennsylvania a high-efficiency air conditioner alone can get you up to $300, and a high-efficiency complete HVAC system can see up to $1000. Maryland's incentives get up to $1,250, with a $100 rebate on a tune up of an existing system.
If you believe that the ac not working or you’re getting little or no cold air, check these three things first. Make sure all the registers in the house are wide open. Then be sure the furnace filter is clean. Then go outside and clean off the condenser coils (Photo 2). If several registers were closed or the filter was clogged, the reduced airflow could have caused the evaporator coil to ice up and stop cooling your home. If you’ve changed the filter and opened all the registers and you’re still not getting airflow at the registers, deice the A-coil. Move the thermostat mode switch from “Cooling” to “Off” and move the fan switch from “Auto” to “On.” Let the blower run for at least 30 minutes or until there’s good airflow at the registers. Then turn the AC back on to test it. If it works for the next 12 hours, you’ve solved the problem.
Has another company told you that your furnace has a cracked heat exchanger? The heat exchanger is the heart of your furnace. Its failure can result in a dangerous situation for your home and the best solution is usually a new furnace. Because of these issues, Bonney takes this situation very seriously. We will offer you proof of the cracked heat exchanger in the form of a picture from our video inspection camera or a report from our exhaust gas analyzer, before we make our recommendation.
R-22 Freon is being phased out & isn't readily available. So the service company may only purchase as needed and the lack of availability would make their cost high. But, as long as they can get it, whatever the cost, unfortunately, is less expensive than replacing the A/C. Which will be the case eventually since it's no longer manufactured or sooner as in my case with a not so old a/c that sprang a leak, that would have been just a repair, but since it uses R-22 the whole unit has to be upgraded(replaced).
A multi-split system is a conventional split system, which is divided into two parts (evaporator and condenser) and allows cooling or heating of several rooms with one external unit. In the outdoor unit of this air conditioner there is a more powerful compressor, ports for connecting several traces and automation with locking valves for regulating the volume of refrigerant supplied to the indoor units located in the room.
The use of furnaces, space heaters, and boilers as a method of indoor heating could result in incomplete combustion and the emission of carbon monoxide, nitrogen oxides, formaldehyde, volatile organic compounds, and other combustion byproducts. Incomplete combustion occurs when there is insufficient oxygen; the inputs are fuels containing various contaminants and the outputs are harmful byproducts, most dangerously carbon monoxide, which is a tasteless and odorless gas with serious adverse health effects.
If your home is not heated using forced air, chances are a boiler will make sure you stay warm during cold nights. A hot water system delivers hot water through a network of pipes that run to every room in your house. The heating effect gets maximized through radiators. The most common issues with hot water heating tend to be not be major, but small problems that add up over time. Mineral deposits within the water tank, a pilot light malfunction, or an issue with a radiator itself can require professional repair. On average, you will pay between $183 and $582 for these problems. The exact amount will depend on the exact problem, as described in our boiler repair cost guide.
Electronically Commutated (EC) fans use brushless DC motors which include in-built electronics to convert the AC supply to DC without the need for a separate DC supply. EC fans provide a more efficient (up to 30%) means of airflow through Precision Air Conditioning (PAC) units with the additional benefit of variable speed control via an output signal from the unit controller. Also see EC Fan upgrades.
Heaters are appliances whose purpose is to generate heat (i.e. warmth) for the building. This can be done via central heating. Such a system contains a boiler, furnace, or heat pump to heat water, steam, or air in a central location such as a furnace room in a home, or a mechanical room in a large building. The heat can be transferred by convection, conduction, or radiation.
Natural ventilation is the ventilation of a building with outside air without using fans or other mechanical systems. It can be via operable windows, louvers, or trickle vents when spaces are small and the architecture permits. In more complex schemes, warm air is allowed to rise and flow out high building openings to the outside (stack effect), causing cool outside air to be drawn into low building openings. Natural ventilation schemes can use very little energy, but care must be taken to ensure comfort. In warm or humid climates, maintaining thermal comfort solely via natural ventilation might not be possible. Air conditioning systems are used, either as backups or supplements. Air-side economizers also use outside air to condition spaces, but do so using fans, ducts, dampers, and control systems to introduce and distribute cool outdoor air when appropriate.
Another precaution you can take to prolong the life of your central air unit is to cover it up during winter. Protect it from ice and snow by putting a sheet of plastic or wood on top of the unit. However, only cover the top and not the whole machine. You don't want to trap moisture that could cause it to rust and you don't want to provide a hiding spot for pests.
Inside the unit, the air passes over the evaporator coil first, and is cooled and dehumidified. The now dehumidified, cold air then passes over the condenser coil where it is warmed up again. Then the air is released back into the room. The unit produces warm, dehumidified air and can usually be placed freely in the environment (room) that is to be conditioned.
While there's nothing you can do to guarantee your air conditioner or furnace will never need repairs, there are ways to take better care of your system. Changing out the air filters every 3-6 months, making sure nothing is obstructing or interfering with the outside unit, and keeping all vents unblocked in well-used rooms will help keep your air conditioning and heating system operating efficiently.