The Rack Cooling Index (RCI) is a metric that measures the percentage of racks in the data centre where the air inlet temperature is at the recommended or allowable level under the guidelines put forth by ASHRAE. RCI (hi) is the metric for racks at the upper limit and RCI (lo) for racks at the lower limit. This metric reveals how uniformly and efficiently a data centre is being cooled.
If you believe that the ac not working or you’re getting little or no cold air, check these three things first. Make sure all the registers in the house are wide open. Then be sure the furnace filter is clean. Then go outside and clean off the condenser coils (Photo 2). If several registers were closed or the filter was clogged, the reduced airflow could have caused the evaporator coil to ice up and stop cooling your home. If you’ve changed the filter and opened all the registers and you’re still not getting airflow at the registers, deice the A-coil. Move the thermostat mode switch from “Cooling” to “Off” and move the fan switch from “Auto” to “On.” Let the blower run for at least 30 minutes or until there’s good airflow at the registers. Then turn the AC back on to test it. If it works for the next 12 hours, you’ve solved the problem.
Its unique feature is the presence of one main external unit that connected to several indoor units. Such systems might be the right solution for maintaining the microclimate in several offices, shops, large living spaces. Just few of outdoor units do not worsen the aesthetic appearance of the building.The main external unit can be connected to several different indoor types: floor, ceiling, cassette, etc.