Hospital operating theatres, in which air is filtered to high levels to reduce infection risk and the humidity controlled to limit patient dehydration. Although temperatures are often in the comfort range, some specialist procedures, such as open heart surgery, require low temperatures (about 18 °C, 64 °F) and others, such as neonatal, relatively high temperatures (about 28 °C, 82 °F).
In the case of direct expansion equipment, the air passing over the indoor cooling coil heats the cold liquid refrigerant. Heating the refrigerant causes boiling and transforms the refrigerant from a cold liquid to a warm gas. This warm gas (or vapor) is pumped from the cooling coil to the compressor through a copper tube (suction line to the compressor) where the warm gas is compressed. In some cases, an accumulator is placed between the cooling coil and the compressor to capture unused liquid refrigerant and ensures that only vapor enters the compressor. The compression process increases the pressure of the refrigerant vapor and significantly increases the temperature of the vapor. The compressor pumps the vapor through another heat exchanger (outdoor condenser) where heat is rejected and the hot gas is condensed to a warm high pressure liquid. This warm high pressure liquid is pumped through a smaller copper tube (liquid line) to a filter (or filter/dryer) and then on to an expansion device where the high pressure liquid is reduced to a cold, low pressure liquid. The cold liquid enters the indoor cooling coil and the process repeats.
Central, "all-air" air-conditioning systems (or package systems) with a combined outdoor condenser/evaporator unit are often installed in North American residences, offices, and public buildings, but are difficult to retrofit (install in a building that was not designed to receive it) because of the bulky air ducts required. (Minisplit ductless systems are used in these situations.) Outside of North America, packaged systems are only used in limited applications involving large indoor space such as stadiums, theatres or exhibition halls.
In a chilled water system, liquid water is pumped throughout the building to “chilled water coils”. Since the liquid water needs to be at a cold temperature, a “cooling plant” is required. The plant is typically referred to as a chiller plant. Vapor compression equipment in the plant, similar to that described in “How does my AC work”, cool water to a cold temperature and pump the cold water to air-to-water heat exchangers where needed.
The heat-exchanger cools the air that is being forced through it by the furnace blower. As the warm air comes in contact with this cool surface the water in the air condenses. By pulling the water molecules from the air. According to the psychometric chart as relative humidity decreases in order to feel cool you will have to lower the temperature even more. A common way to counteract this effect is by installing a whole-home humidifier. Similarly, installing a high efficient system this need to turn the temperature down wont have such and influence on your energy costs.
In the United States, HVAC engineers generally are members of the American Society of Heating, Refrigerating, and Air-Conditioning Engineers (ASHRAE), EPA Universal CFC certified (for installation and service of CFC HVAC devices), or locally engineer certified such as a Special to Chief Boilers License issued by the state or, in some jurisdictions, the city. ASHRAE is an international technical society for all individuals and organizations interested in HVAC. The Society, organized into regions, chapters, and student branches, allows exchange of HVAC knowledge and experiences for the benefit of the field's practitioners and the public. ASHRAE provides many opportunities to participate in the development of new knowledge via, for example, research and its many technical committees. These committees typically meet twice per year at the ASHRAE Annual and Winter Meetings. A popular product show, the AHR Expo, is held in conjunction with each winter meeting. The Society has approximately 50,000 members and has headquarters in Atlanta, Georgia.
They are also often harder to install. A proper location on the roof must be selected that can support the weight of the unit. Then a platform must be built and a drain pipe for the unit must be run along the roof to avoid problems with mold and corrosion. A crane must be used to lift the unit onto the roof while a team guides it into place and hooks it up.
Installing a split system may involve making modifications to the house itself for the necessary lines to be run. The heat exchangers are also more prone to picking up debris and must be cleaned on a regular basis. While they come with protective screens over the fan, care must still be taken to ensure that nothing gets in, especially in a home with children.
©2018 By Horizon Services, LLC. All Rights Reserved. DE License # PL0000726, HL0000299. Contractor Reg. # PA017876, PA057742. NJ Plumbing Lic. # PL36BI01232300 - David Geiger HIC reg. # 13VH05117300, NJ Master HVACR contractor Lic. # 19HC00193700. MD Master HVACR contractor Lic. # 47186, MD Master Plumber/Gas Fitter Lic. # 63739 – David Geiger. EL.LIC./B.P. #34EI01207700.
A specialized air conditioner that is used only for dehumidifying is called a dehumidifier. It also uses a refrigeration cycle, but differs from a standard air conditioner in that both the evaporator and the condenser are placed in the same air path. A standard air conditioner transfers heat energy out of the room because its condenser coil releases heat outside. However, since all components of the dehumidifier are in the same room, no heat energy is removed. Instead, the electric power consumed by the dehumidifier remains in the room as heat, so the room is actually heated, just as by an electric heater that draws the same amount of power.
Even if your air conditioning unit is still working, depending on the type of system in your home today, you could recoup your investment in a new system in as little as three years. However, that doesn't mean that your system needs to be replaced. Furnaces, air conditioners, and other heating and cooling systems have made tremendous gains in efficiency over the past five years, so if you have an older unit, it is worth taking a look at whether or not a repair is the best investment.