A more efficient method of controlling humidity is to use the waste heat from the refrigeration cycle itself. Instead of rejecting the waste heat outdoors, the heat is directed inside when humidity control is required. One form of heat reclaim is called hot-gas reheat or “refrigerant desuperheating” where refrigerant is passed through a heat exchanger located downstream of the cooling coil. The hot high pressure vapor leaving the compressor passes through this heat exchanger prior to entering the condenser coil. This in turn heats the indoor air and again causes the AC system to run longer to meet the thermostat set point. Although more energy is used, this is much more efficient than turning on an electric heater. Another form of heat reclaim is called sub-cool reheat. This strategy takes the warm liquid refrigerant from the condenser and passes it through a heat exchanger located downstream of the cooling coil. Less heat is available using this method because the majority of the heat has already been rejected at the condenser. Since more energy is used to pump liquid (as opposed to a gas) through the heat exchanger it would appear that this method is less efficient than the hot-gas method, however, the liquid in the heat exchanger is sub-cooled in the cold supply air stream which increases the capacity of the air conditioner. Since more capacity is available, the AC units is able to meet the thermostat more quickly.
As a Carrier® dealer, with a wide variety of products to choose from, we can keep your family healthy and feeling comfortable all year long. We carry a complete line of indoor comfort equipment with innovations that raise the standards of comfort and reliability, including air conditioners, heat pumps, gas furnaces, programmable thermostats, humidifiers, ductless split systems, geothermal systems, boilers, air cleaners, ultra violet lights, ventilators and zoning products. Let the experts at Dunes Heating and Air Conditioning, LLC help you customize a solution that's right for you.
Air handlers and furnaces aren't often found together. If you have a furnace you probably don't need to think about an air handler. Air handlers tend to be paired up with heat pumps and help manage air flow throughout the building. Some models also provide secondary heating and cooling parts to help out the heat pump. A furnace works on a different concept. Instead of an air handler, furnaces have included blowers that move the warmed air into your ventilation and disperse through your home. Since furnaces have combustion chambers and create heat, they don't have some of the parts you'll find in a typical air handler.
While repair is often the preferred choice, problems like a consistent repeating complication or extra-costly furnace repair parts might start leading you in a different direction. Remember that repair is only the preferred option when the cost of seeking it makes sense! If you’re shelling out for repair every single year, then it might be time to talk to your heating contractor about furnace replacement.
Who do you call when you have a HVAC related issue? How do you know that you’re making a call to the right team? Much of Cary has come to trust us here at Service Experts Heating & Air Conditioning for all their heating and air conditioning needs. Our qualified technicians know what they’re doing. No matter your problem or question, our team is able to help—no issue is too big or too small in Cary. You can feel comfortable in your decision to call Service Experts and know that you’re working with a team that has your back.
Feel perfectly comfortable at home with our innovative Lennox Residential heating, cooling and air quality systems. Lennox manufactures high-efficiency HVAC systems including furnaces and air conditioners designed to conserve energy and save money. Our complementing air filtration systems, humidifiers and dehumidifiers help keep indoor air quality healthy and clean.
To clean your air conditioner drain, first shut off the power to your unit at both the thermostat and the breaker. Then remove the drain pan. If the pan is full of water, soak up the liquid with a few towels or rags or use a wet vacuum. You can use a solution of water and distilled vinegar, or substitute peroxide for the vinegar, to clean out the drain pipe. Let the pipe sit for a while in the solution and then put all the parts back in place. Once you start using your air conditioner on a regular basis, check it periodically to ensure condensation isn't building up.
You've probably noticed many appliances boasting an Energy Star Certification. What this means is that manufacturer voluntarily built the product to help reduce greenhouse gases and meet non-regulatory guidelines offered by the Environmental Protection Agency. To earn an Energy Star rating, a product or system must be tested by a third party that has been recognized by the EPA for meeting their testing qualifications.
Air Conditioning Parts is an international AC Parts distributor specializing in OEM wholesale A/C Parts for all air conditioner makes and models. All of our parts and equipment are available at factory direct pricing! For almost 30 years, our exceptional level of service and responsiveness coupled with our experienced air conditioning parts specialists have allowed us to establish solid long term relationships with thousands of A/C service companies, hotel and motel owners, apartment owners and management companies, and numerous other industry professionals who need and count on a knowledgeable AC parts supplier for the right part, overnight delivery and the best possible prices for all types of air conditioning parts and AC equipment. Professionals know they can depend on Air Conditioner Parts! Let us earn your trust. Call us for any A/C Part or any A/C Equipment at 800-525-3572.
The three major functions of heating, ventilation, and air conditioning are interrelated, especially with the need to provide thermal comfort and acceptable indoor air quality within reasonable installation, operation, and maintenance costs. HVAC systems can be used in both domestic and commercial environments. HVAC systems can provide ventilation, and maintain pressure relationships between spaces. The means of air delivery and removal from spaces is known as room air distribution.
Vredevoogd Heating & Cooling Grand Rapids values each and every customer. Servicing or installing your HVAC system means establishing a service relationship with each homeowner. We promise to earn your trust with our consummate level of professionalism and expert service. We back our work with the strongest industry guarantees because we value your continued business.
Air conditioners often use a fan to distribute the conditioned air to an occupied space such as a building or a car to improve thermal comfort and indoor air quality. Electric refrigerant-based AC units range from small units that can cool a small bedroom, which can be carried by a single adult, to massive units installed on the roof of office towers that can cool an entire building. The cooling is typically achieved through a refrigeration cycle, but sometimes evaporation or free cooling is used. Air conditioning systems can also be made based on desiccants (chemicals which remove moisture from the air) and subterraneous pipes that can distribute the heated refrigerant to the ground for cooling.
Because an air conditioner moves heat between the indoor coil and the outdoor coil, both must be kept clean. This means that, in addition to replacing the air filter at the evaporator coil, it is also necessary to regularly clean the condenser coil. Failure to keep the condenser clean will eventually result in harm to the compressor, because the condenser coil is responsible for discharging both the indoor heat (as picked up by the evaporator) and the heat generated by the electric motor driving the compressor.
AC units and thermostats have built-in delay features when they’re shut down and then repowered. The delay can be as long as 10 minutes. And, if you’ve subscribed to an energy-saving device from your local power utility, the unit can take even longer to reset. If you’ve installed the parts shown and reinstalled the disconnect block, repowered the circuit breaker, turned on the switch at the furnace, moved the thermostat to AC mode and lowered the temperature below the indoor temperature, and the unit doesn’t fire up after 30 minutes, it’s time to call a pro.
Humidity is becoming more of a concern to building operators and owners. High indoor humidity leads to mold and mildew growth inside the building. The are several methods of controlling indoor humidity. The simplest (and most expensive) method is to connect a humidistat to an electric heater. When the humidity inside the building rises above the humidistat set point, the heater is turned on. The additional heat causes the air conditioning system to run longer and remove more moisture.
The performance of vapor compression refrigeration cycles is limited by thermodynamics. These air conditioning and heat pump devices move heat rather than convert it from one form to another, so thermal efficiencies do not appropriately describe the performance of these devices. The Coefficient-of-Performance (COP) measures performance, but this dimensionless measure has not been adopted. Instead, the Energy Efficiency Ratio (EER) has traditionally been used to characterize the performance of many HVAC systems. EER is the Energy Efficiency Ratio based on a 35 °C (95 °F) outdoor temperature. To more accurately describe the performance of air conditioning equipment over a typical cooling season a modified version of the EER, the Seasonal Energy Efficiency Ratio (SEER), or in Europe the ESEER, is used. SEER ratings are based on seasonal temperature averages instead of a constant 35 °C (95 °F) outdoor temperature. The current industry minimum SEER rating is 14 SEER.
You can usually slip the belt on the motor’s (smaller) pulley first and then start it on the blower pulley. Rotate the blower pulley by hand, holding the belt in place but keeping your fingers from getting caught between the belt and the pulley. The belt should slip right into place. If it seems to be too tight or difficult to set in place, it may be necessary to adjust the motor mount to provide more slack.