If summertime temperatures leave you hot under the collar, you’re not alone. More than 75 percent of U.S. homes use air conditioning, and 90 percent of new homes are equipped with central air. And eco-conscious consumers will be gratified to know that today’s air conditioners are more energy-efficient, which means they cost less to run while keeping you cool and comfortable.
Heat pipe heat exchangers or run-around coils perform a similar function when humidity control is required. Two heat exchanger are placed in the air stream, one upstream of the cooling coil and the other downstream of the cooling coil. These heat exchangers are connected together with piping. A heat transfer fluid, whether it be water or refrigerant, is either pumped or gravity fed from one heat exchanger to the other. The heat exchanger down stream of the cooling coil (re-heat coil) cools the liquid medium inside the heat exchanger and heats the air passing over the heat exchanger. The cold liquid inside the heat exchanger is moved to the heat exchanger upstream of the cooling coil (pre-cool coil) where it pre-cools the air passing over the heat exchanger and warms the liquid passing through the heat exchanger. The affect of a heat pipe or run-around coil is to reduce the sensible heat capacity of the AC system. The latent capacity of the AC system increases if direct-expansion equipment is used or remains relatively constant if chilled water equipment is used. Since the sensible capacity of the AC system has been reduced, the system must run longer to meet the thermostat set point thereby removing more moisture.
Ventilating or ventilation (the V in HVAC) is the process of exchanging or replacing air in any space to provide high indoor air quality which involves temperature control, oxygen replenishment, and removal of moisture, odors, smoke, heat, dust, airborne bacteria, carbon dioxide, and other gases. Ventilation removes unpleasant smells and excessive moisture, introduces outside air, keeps interior building air circulating, and prevents stagnation of the interior air.
Relative humidity is the ratio of the partial pressure of water vapour in an air-water mixture to the saturated vapour pressure of water at a prescribed temperature. In prevailing Northern European conditions relative humidity and percentage saturation (ration of moisture content) can be considered the same as the divergence is <1%. In high temperature areas they should be treated differently as the divergence may be as high as 10%.
Dunes Heating And Air Conditioning is HVAC Contractor providing the best possible Heating and Air Conditioning Repair, maintenance and installation for your home or business in Mount Pleasant, Charleston and Isle of Palms South Carolina. You can count on us to provide you with a system and solution that fits your unique needs and since we've installed many systems in this area, we've earned a reputation for doing the job right the first time.
A more efficient method of controlling humidity is to use the waste heat from the refrigeration cycle itself. Instead of rejecting the waste heat outdoors, the heat is directed inside when humidity control is required. One form of heat reclaim is called hot-gas reheat or “refrigerant desuperheating” where refrigerant is passed through a heat exchanger located downstream of the cooling coil. The hot high pressure vapor leaving the compressor passes through this heat exchanger prior to entering the condenser coil. This in turn heats the indoor air and again causes the AC system to run longer to meet the thermostat set point. Although more energy is used, this is much more efficient than turning on an electric heater. Another form of heat reclaim is called sub-cool reheat. This strategy takes the warm liquid refrigerant from the condenser and passes it through a heat exchanger located downstream of the cooling coil. Less heat is available using this method because the majority of the heat has already been rejected at the condenser. Since more energy is used to pump liquid (as opposed to a gas) through the heat exchanger it would appear that this method is less efficient than the hot-gas method, however, the liquid in the heat exchanger is sub-cooled in the cold supply air stream which increases the capacity of the air conditioner. Since more capacity is available, the AC units is able to meet the thermostat more quickly.
Repair Clinic’s gas furnace troubleshooting guide will walk you through the steps necessary for diagnosing your furnace problem. Start with our list of symptoms. When you find the right one, we’ll show you the common causes. Enter your model number into the search field and you’ll know which part to buy. We can even show you how to install it. Where else can you find online furnace troubleshooting help like this?
In 1992, a non-governmental organization, Greenpeace, was spurred by corporate executive policies and requested that a European lab find substitute refrigerants. This led to two alternatives, one a blend of propane (R290) and isobutane (R600a), and one of pure isobutane. Industry resisted change in Europe until 1993, and in the U.S. until 2011, despite some supportive steps in 2004 and 2008 (see Refrigerant Development above).
At Horizon Services, we strive to go above and beyond for every one of our clients. We offer honest, upfront pricing in writing for every service we provide, as well as flexible scheduling to suit your needs, industry leading warranties, and a 100% customer satisfaction guarantee. When you call on us for heating services, our technicians will arrive on-time, every time. If we're even one minute later than the provided window of time, you don't pay. We understand that dealing with a broken or malfunctioning heating system can be incredibly frustrating. Let us turn your stressful situation into a thing of the past!
Getting one of the best air conditioner brands is important whether you’re replacing an old HVAC system, or having the first AC unit system put in your brand new home, but it’s not everything. The best Trane, Ruud, or American Standard HVAC system won’t perform any better than a no-name bargain air conditioner system if it’s not installed properly by a quality HVAC contractor. It’s important to find an HVAC installation professional with high ratings and expert knowledge within the field so that your top brand can perform at optimal efficiency. Furnace Repair Click Here